|Place of Origin:||China|
|Model Number:||XW-2HP, XW-3HP, XW-5HP|
|Minimum Order Quantity:||1|
|Packaging Details:||Wooden Case|
|Delivery Time:||15 working days|
|Payment Terms:||L/C, D/A, D/P, T/T, Western Union, MoneyGram|
|Supply Ability:||500 sets/month|
|Product Name:||Industrial Water Chiller||Application:||Industrial Cooling Solutions|
|MOQ:||1 Set||Cooling Type:||Air Cooled Condenser Chiller|
|Production Time:||15-20 Days||Keyword:||Easy Operation|
|After Warranty Service:||Video Technical Support, Online Support And Spare Parts||After-sales Service Provided:||Free Spare Parts, Field Installation, Commissioning And Training|
Cw5000 Chilled Water System,
Small Laser Chilled Water System,
Cw 5200 Water Chiller
Cw5000 Cw 5200 Small Laser Active Aqua Chill Chilled Water System Water Chiller
Industrial water chiller is mainly suitable for plastic and mechanical processing. It can accurately control the temperature of plastic’s forming mold to shorten the molding cycle and speed up the product shaping; this series uses the principle of cold and heat exchange for cooling, which can be cooled quickly and the temperature control is stable. And not affected by environmental factors, it is an indispensable configuration equipment in modern industry.
|cooling Fans Number||1 set||2 sets||2 sets|
|Pump Flow Rate||100L(min)||100L(min)||50L/min|
|Temperature Control Range||5℃-35℃||5℃-35℃||5℃-35℃|
1. Using high quality computer board, the temperature is accurate to ±1℃.
2. Using Germany Schneider AC contactor and phase sequence relay.
3. Using ALCO filters.
4. Using American YK306F pressure controller.
Choose a stable foundation for convenient installation and maintenance, it must be open surroundings, unobstructed, without corrosion, pollution, sun, rain. Choose a suitable cooling tower in accordance with the cooling capacity of the chiller. Install the piping of the chiller according to the size of the throat of the machine. Do not reduce the size of the cooling water pipe. This will cause high pressure overload, affecting the cooling effect and increase power consumption. The air-cooled chiller must be installed at a minimum distance of 1 meter against wall. For outdoor position, the rain-proof facilities must be provided.
Note: 1). The power load and grounding part should be constructed in accordance with relevant laws and regulations!
2). The chilled water pipe of the newly installed chiller must be covered with an insulation layer!
Schematic Diagram of Air-cooled Chiller
1. compressor 2. High pressure meter 3. High voltage protector 4. Condenser 5. Cooling fan 6. Filter drier 7. Capillary (expansion valve) 8. Evaporato 9. Water pump 10. Low pressure meter 11. Low voltage protector 12-13. Waterway valve
Frequently Asked Questions