|Place of Origin:||China|
|Model Number:||XW-2HP, XW-3HP, XW-5HP|
|Minimum Order Quantity:||1|
|Packaging Details:||Wooden Case|
|Delivery Time:||15 working days|
|Payment Terms:||L/C, D/A, D/P, T/T, Western Union, MoneyGram|
|Supply Ability:||500 sets/month|
|Product Name:||Industrial Water Chiller||Application:||Industriy|
|MOQ:||1 Set||Cooling Type:||Cooled Water Circulating|
|Production Time:||15-20 Days||Usage:||Injection Molding Cooling Machine|
|After Warranty Service:||Video Technical Support, Online Support And Spare Parts||After-sales Service Provided:||Free Spare Parts, Field Installation, Commissioning And Training|
1Hp Chilled Water Cooler,
Cw5000 Industrial Water Chiller,
3Ton Industrial Water Chiller
1 Hp Chilled Water Cooler Cw5000 2 3 Ton Water Cooled Industrial Water Chiller
Industrial water chiller is mainly suitable for plastic and mechanical processing. It can accurately control the temperature of plastic’s forming mold to shorten the molding cycle and speed up the product shaping; this series uses the principle of cold and heat exchange for cooling, which can be cooled quickly and the temperature control is stable. And not affected by environmental factors, it is an indispensable configuration equipment in modern industry.
|cooling Fans Number||1 set||2 sets||2 sets|
|Pump Flow Rate||100L(min)||100L(min)||50L/min|
|Temperature Control Range||5℃-35℃||5℃-35℃||5℃-35℃|
1. High efficiency foil aluminum fin condenser.
2. Tank coil evaporator (copper tube).
3. Using Stainless steel water tank.
4. Complete protection functions (phase loss, reverse phase, over temperature, high and low pressure, overload).
5. Using high quality computer board, the temperature is accurate to ±1℃.
6. Using Germany Schneider AC contactor and phase sequence relay.
7. Using ALCO filters.
8. Using American YK306F pressure controller.
Solutions for Poor Heat Dissipation
When the condenser heat dissipation is poor, the compressor efficiency is low and the operating current increases. When the air-cooled high-pressure rises to 24kg/cm2, or the water-cooled high-pressure rises to 20kg/cm2, the compressor trips under the protection of the high-pressure switch, and stops running. Upon poor heat dissipation, high pressure overload and fault code or fault indication, please check whether the circulating water of the cooling tower is normal, whether the cooling water temperature is too high, whether the cooling tower fan pump is running, and whether the cooling water valve is fully opened (please check for air-cooled type) Whether the radiator is dirty or blocked, after the above is normal, press the reset button (REST) or shut down and restart to operate normally. If high pressure overload occurs frequently, please arrange to clean the condenser as soon as possible.
Installation Diagram of Air-cooled Chiller
Frequently Asked Questions