|Place of Origin:||China|
|Model Number:||XW-2HP, XW-3HP, XW-5HP|
|Minimum Order Quantity:||1|
|Packaging Details:||Wooden Case|
|Delivery Time:||15 working days|
|Payment Terms:||L/C, D/A, D/P, T/T, Western Union, MoneyGram|
|Supply Ability:||500 sets/month|
|Product Name:||Industrial Water Chiller||Application:||Industriy|
|MOQ:||1 Set||Cooling Type:||Air Cooled Condenser Chiller|
|Production Time:||15-20 Days||Feature:||Cost Effective|
|After Warranty Service:||Video Technical Support, Online Support And Spare Parts||After-sales Service Provided:||Free Spare Parts, Field Installation, Commissioning And Training|
Cw3000 Water Cooled Chiller,
Recirculating Active Water Cooled Chiller,
1Ton Industrial Water Chiller
1 Ton Recirculating Active Aqua Inline Cw 5000 Mini Cw3000 Water Cooled Chiller
Industrial water chiller is mainly suitable for plastic and mechanical processing. It can accurately control the temperature of plastic’s forming mold to shorten the molding cycle and speed up the product shaping; this series uses the principle of cold and heat exchange for cooling, which can be cooled quickly and the temperature control is stable. And not affected by environmental factors, it is an indispensable configuration equipment in modern industry.
|cooling Fans Number||1 set||2 sets||2 sets|
|Pump Flow Rate||100L(min)||100L(min)||50L/min|
|Temperature Control Range||5℃-35℃||5℃-35℃||5℃-35℃|
1. High efficiency foil aluminum fin condenser.
2. Tank coil evaporator (copper tube).
3. Using Stainless steel water tank.
4. Complete protection functions (phase loss, reverse phase, over temperature, high and low pressure, overload).
5. Using high quality computer board, the temperature is accurate to ±1℃.
6. Using Germany Schneider AC contactor and phase sequence relay.
7. Using ALCO filters.
8. Using American YK306F pressure controller.
Method of Operation
Before the trial run, make sure the following items are correct:
1). Fill the freezing water tank with water or other freezing medium before starting the water pump; (Note: Please choose the proper freezing medium as required)
2). Please pay attention to the running direction of the water pump and whether the water tower fan is reversed (if the water pump is three-phase, any two of the power phase lines must be exchanged for reversal, and then the switch should be closed after the connection is completed).
Schematic Diagram of Water-cooled Chiller
1. compressor 2. High pressure meter 3. High voltage protector 4. Condenser 5. Filter drier 6. Capillary (expansion valve) 7. Evaporator 8. Chilled water pumps 9. Low pressure meter 10. Low voltage protector 11. Cooling water pump 12. cooling tower 13-14. Waterway valve 15-16. Waterway valv
Frequently Asked Questions