|Place of Origin:||China|
|Model Number:||XW-2HP, XW-3HP, XW-5HP|
|Minimum Order Quantity:||1|
|Packaging Details:||Wooden Case|
|Delivery Time:||15 working days|
|Payment Terms:||L/C, D/A, D/P, T/T, Western Union, MoneyGram|
|Supply Ability:||500 sets/month|
|Product Name:||Industrial Water Chiller||Application:||Industriy|
|MOQ:||1 Set||Cooling Type:||Cooled Water Circulating|
|Production Time:||15-20 Days||Feature:||Cost Effective|
|After Warranty Service:||Video Technical Support, Online Support And Spare Parts||After-sales Service Provided:||Free Spare Parts, Field Installation, Commissioning And Training|
5200 Carrier Industrial Water Chiller,
2000Liter Industrial Water Chiller,
R22 Water Cooled Chiller
2000 Liter 3000 5000 5200 Carrier Water Cooled Industrial Water Chiller For Sale
Industrial water chiller is mainly suitable for plastic and mechanical processing. It can accurately control the temperature of plastic’s forming mold to shorten the molding cycle and speed up the product shaping; this series uses the principle of cold and heat exchange for cooling, which can be cooled quickly and the temperature control is stable. And not affected by environmental factors, it is an indispensable configuration equipment in modern industry.
|cooling Fans Number||1 set||2 sets||2 sets|
|Pump Flow Rate||100L(min)||100L(min)||50L/min|
|Temperature Control Range||5℃-35℃||5℃-35℃||5℃-35℃|
1. High efficiency foil aluminum fin condenser.
2. Tank coil evaporator (copper tube).
3. Using Stainless steel water tank.
4. Complete protection functions (phase loss, reverse phase, over temperature, high and low pressure, overload).
5. Using high quality computer board, the temperature is accurate to ±1℃.
6. Using Germany Schneider AC contactor and phase sequence relay.
7. Using ALCO filters.
8. Using American YK306F pressure controller.
1). The chilled water pump cannot be operated without water in the water tank;
2). Please try to avoid frequent turning on/off the operating switch;
3). When the freezing water temperature reaches the set degree, the compressor will automatically stop running, which is a normal phenomenon;
4). Avoid setting the temperature switch below 5°C to prevent the evaporator from freezing; (except for low-temperature chillers)
5). In order to ensure the cooling effect and maintain the best condition, please clean the condenser, evaporator and water filter regularly.
Installation Diagram of Air-cooled Chiller
Frequently Asked Questions