|Place of Origin:||China|
|Model Number:||XW-2HP, XW-3HP, XW-5HP|
|Minimum Order Quantity:||1|
|Packaging Details:||Wooden Case|
|Delivery Time:||15 working days|
|Payment Terms:||L/C, D/A, D/P, T/T, Western Union, MoneyGram|
|Supply Ability:||500 sets/month|
|Product Name:||Industrial Water Chiller||Application:||Industriy|
|MOQ:||1 Set||Cooling Type:||Air Cooled Condenser Chiller|
|Production Time:||15-20 Days||Usage:||Injection Molding Cooling Machine|
|After Warranty Service:||Video Technical Support, Online Support And Spare Parts||After-sales Service Provided:||Free Spare Parts, Field Installation, Commissioning And Training|
Centrifugal Cold Industrial Water Chiller,
5Ton Industrial Water Chiller,
Ice Bath Cw 5000 Water Chiller
Cw 5000 5 Ton Water Cooled Centrifugal Cold Industrial Water Chiller
Industrial water chiller is mainly suitable for plastic and mechanical processing. It can accurately control the temperature of plastic’s forming mold to shorten the molding cycle and speed up the product shaping; this series uses the principle of cold and heat exchange for cooling, which can be cooled quickly and the temperature control is stable. And not affected by environmental factors, it is an indispensable configuration equipment in modern industry.
|cooling Fans Number||1 set||2 sets||2 sets|
|Pump Flow Rate||100L(min)||100L(min)||50L/min|
|Temperature Control Range||5℃-35℃||5℃-35℃||5℃-35℃|
1. High efficiency foil aluminum fin condenser.
2. Tank coil evaporator (copper tube).
3. Using Stainless steel water tank.
4. Complete protection functions (phase loss, reverse phase, over temperature, high and low pressure, overload).
5. Using high quality computer board, the temperature is accurate to ±1℃.
6. Using Germany Schneider AC contactor and phase sequence relay.
7. Using ALCO filters.
8. Using American YK306F pressure controller.
Solutions for Insufficient Refrigerant and Low Pressure
A. When the water temperature is above 5°C and the pressure of the low pressure gauge is lower than 2kg/cm2, it means that the refrigerant is insufficient. First, the leaking refrigerant should be repaired, and then the filter drier should be replaced to re-evacuate and refill with proper refrigerant.
B. When the leaking refrigerant is found to be immersed in water, please stop the operation of the freezer immediately, remove the water in the water tank as soon as possible, and notify the distributor/manufacturer to deal with and repair as soon as possible, so as to prevent the compressor from sucking water into the system and causing more serious damage.
Installation Diagram of Air-cooled Chiller
Frequently Asked Questions