|Place of Origin:||China|
|Model Number:||XW-2HP, XW-3HP, XW-5HP|
|Minimum Order Quantity:||1|
|Packaging Details:||Wooden Case|
|Delivery Time:||15 working days|
|Payment Terms:||L/C, D/A, D/P, T/T, Western Union, MoneyGram|
|Supply Ability:||500 sets/month|
|Product Name:||Chilled Water System||Application:||Industriy|
|MOQ:||1 Set||Cooling Type:||Air Cooled Condenser Chiller|
|Production Time:||15-20 Days||Usage:||Injection Molding Cooling Machine|
|After Warranty Service:||Video Technical Support, Online Support And Spare Parts||After-sales Service Provided:||Free Spare Parts, Field Installation, Commissioning And Training|
Compact Industrial Water Chiller,
Benchtop Industrial Water Chiller,
Benchtop Water Cooled Industrial Chiller
Process Best Compact Water Cooled Industrial Benchtop Water Chiller
Industrial water chiller is mainly suitable for plastic and mechanical processing. It can accurately control the temperature of plastic’s forming mold to shorten the molding cycle and speed up the product shaping; this series uses the principle of cold and heat exchange for cooling, which can be cooled quickly and the temperature control is stable. And not affected by environmental factors, it is an indispensable configuration equipment in modern industry.
|cooling Fans Number||1 set||2 sets||2 sets|
|Pump Flow Rate||100L(min)||100L(min)||50L/min|
|Temperature Control Range||5℃-35℃||5℃-35℃||5℃-35℃|
1. High efficiency foil aluminum fin condenser.
2. Tank coil evaporator (copper tube).
3. Using Stainless steel water tank.
4. Complete protection functions (phase loss, reverse phase, over temperature, high and low pressure, overload).
5. Using high quality computer board, the temperature is accurate to ±1℃.
6. Using Germany Schneider AC contactor and phase sequence relay.
7. Using ALCO filters.
8. Using American YK306F pressure controller.
The compressor cannot start while the fault indicator and protection switch are in normal condition, please check:
a. Whether the temperature switch is adjusted too high or damaged;
b. Whether the switch is damaged;
c. Whether the anti-freeze switch is damaged;
d. Whether the pressure switch is tripped or damaged;
e. Whether the compressor overload protector is damaged or tripped;
f. Whether the coil of the electromagnetic relay is damaged or whether the overload protector is damaged;
g. Whether the liquid level in the water tank is too low;
h. Whether the frozen water flow switch is damaged. The compressor cannot run if either of the above control switch or circuit is faulty.
Installation Diagram of Air-cooled Chiller
Frequently Asked Questions